|Home||Search||Pollutants||About the Database|
|LDEQ Incident Number
|Point Source(s)||Notes||Amount of Release|
|DU-5 Naptha Stripper Reboiler [E-1004]||Cause: A leak in the weld of a pipping elbow of the DU-5 Naptha Stripper Reboiler caused by internal corrosion on the reboiler.|
Notes: RQ. Reportable quantities were exceeded for 8 chemicals including Ethane, Methane, Toulene, and n-Hexane. Refinery report states that "immediately following discovery of the leak, the site's emergency response team was activated and the naphtha stripper was blocked in and depressurized."
|Coker Flare FE-401||Cause: While starting the Coker Jet Pump on 9/29/11 at 6:45pm, the electrical breaker at Motiva's Coking Unit tripped de-energizing the Motor Control Center. Consequently, the Coker Wet Gas Compressor tripped offline therefore resulting in unit flaring and operating in hot circulation mode. Hot circulation mode is an operating mode in which the unit recycles feed at high temperatures. This mode of operation lessens the amount of flaring in comparison to a complete unit shutdown. The initial inspection of the Jet Pump revealed that the auto-transformer serving as a soft start for this pump had failed causing the electrical breaker to trip open. Once repairs were completed, the Coker Unit was safely re-started and flaring stopped.|
Notes: Immediately, Operations placed the furnace F-125 in hot steam standby and brought the Coker Unit into hot circulation mode to prevent additional flaring of non treated gas. Norco maintenance personnel were called out to troubleshoot the trip of the Coker Wet Gas Compressor and related equipment. The auto-transformer was removed from the circuit. Relay coordination was modified in order to protect the new circuit. After troubleshooting, maintenance personnel determined that operations could safely re-start the Coker Process Unit. During this time the Coker Wet Gas Compressor was restarted and flaring stopped. By 12/31/11 a study will be completed to determine whether the auto-transformer can be permanently removed from the system. After this study is completed, a strategy will be created to address the required changes. This action will be completed by 3/31/12. Calculations confirm that the reportable quantity for sulfur dioxide was exceeded as well as the permitted maximum pound per hour emission limits for carbon monoxide, nitrogen oxide, particulate matter, sulfur dioxide, VOC's, 1,3 butadiene, and benzene as a result of the release.
|Flare: EPN 3-84||Cause: A leak occurred at HIC-84, along the downstream block valves, allowing nitrogen to enter the column causing a rapid pressure increase. The distilling unit upper crude column became overpressured, and PCV-195 opened the flare to relieve pressure in the column. EPN 3-84 Flare at Shell was used because the Motiva flare was upset and the pilot light was out. Original upset occurred at Motiva DU-5 Crude Unit with a notrogen leak into the Upper Crude Column.|
Notes: The Shell report for the motiva release was dated May 5th, 2010 instead of 2011.